Is it possible to PA test computers and other IT equipment with the Prime Test 100? I can't see a way to do it without a 500v insulation test.
Anyone using this model on IT equipment?
- Posts: 1
- Joined: Fri Jan 17, 2014 3:17 pm
IT kit shouldn't have any problem with a 500V IR test.
It's the reduced current earth bond test that's the important one.
The 250V IR test was introduced to enable proper testing of surge protected leads, etc.
C&G 2377 -01 & -02
- Posts: 114
- Joined: Tue Feb 08, 2011 3:27 pm
The 500 V DC test is suitable for IT equipment that is CE marked. CE marked IT equipment should comply with the requirements of BS EN60950, which states that the equipment can withstand a dielectric strength test of 1500V r.m.s.
Technical Sales Engineer
- Technical Sales Engineer
- Posts: 3
- Joined: Fri Jul 05, 2013 8:35 am
Return to Portable Appliance Testing
Who is online
Users browsing this forum: Bing [Bot] and 2 guests